"The Intelli-Hood system at Shriner’s is exceeding expected savings, it has the staff very impressed...which makes us look like heroes! We’re pleased with the data and will get it installed in future kitchens. ”
Faced with the industry challenge to reduce operating costs, Shriner’s
Hospital sought after promising opportunities to reduce energy usage.
Other hospitals in the area had selected Demand Control Kitchen
Ventilation (DCKV) for their cafeteria kitchen hoods based on promising
estimated savings and available utility incentives. Shriner’s decided to
also take advantage of the opportunity.
- Total motor power: 8 HP
- Daily operating hours: 14
- Days per week: 7
- Weeks per year: 52
- Cost per kilowatt hour: $0.10
- Climate zone: 5
Shriner’s Hospital made use of $4,000 in total incentives from both People’s Gas and Franklin Energy to get DCKV installed. Intelli-Hood reduced their hood exhaust fan speed by 45 percent and has been proven to perform above expectations.
Below is a sample graph of the varying exhaust fan speed for one day at the hospital:
Could Intelli-Hood be a fit for my project?
Are you curious how much energy Intelli-Hood could save within your commercial or industrial kitchens? Submit an energy savings estimate request form at the bottom of our Intelli-Hood page to get started.
Email this case study or share it to your social media by clicking the icons below.
Most Recent Posts
Meet Nathan Young, Solar & Geo Operations Manager
Author: Allison Sternad – Feb 21, 2018
Geothermal Heat Pump Tax Credits Reinstated Through 2021
Author: Seth Parker – Feb 21, 2018
Love is in the Air (and so are dangerous gases)
Author: Cameron Lenard – Feb 14, 2018
Love What You Do
Author: Craig Davis – Jan 24, 2018