As a part of a kitchen renovation project, Intelli-Hood demand control kitchen ventilation was installed in March of 2017 to save energy and reduce operational costs. The hotel was originally constructed in 1992. The following are operating conditions of the site:
• Total motor power: 17.5 horsepower
• Daily operating hours: 20
• Days per week: 7
• Weeks per year: 52
• Cost per kilowatt hour: .11 €
The system is performing optimally and is projected to deliver return on investment in under a year.
Below is a sample graph of the varying exhaust fan speed for one day at the hotel:
Could Intelli-Hood be a fit for my project?
Are you curious how much energy Intelli-Hood could save within your commercial or industrial kitchens? Submit an energy savings estimate request form at the bottom of our Intelli-Hood page to get started.
Email this case study or share it to your social media by clicking the icons below.
Most Recent Posts
Intelli-Hood Case Study - Corporate Dining
Author: Allison Sternad – Dec 11, 2017
The Advantages of Optical Sensing in Demand Control Kitchen Ventilation Systems
Author: Randy Miles – Nov 30, 2017
Meet Lorie Reese, Project Specialist
Author: Allison Sternad – Nov 13, 2017
Lodging Consumer Dining Trends and your HVAC system
Author: David Keyes – Nov 9, 2017